I am trying to run an example VI using the EthernetIP API for LabVIEW. However, even though the VI is running, it does not seem to read or write data from/to the CompactLogix PLC. No error is occurring in the VI, not even if I change the PLC IP address to a wrong one on purpose.
Verify the Network Path input string is specified with the proper syntax.The syntax for a simple system is <PLC address>,<backplane port number>,<Logix slot number>. For example, 10.0.0.1,1,0 is the routing path for a ControlLogix 5561 with IP address 10.0.0.1 and with the processor in slot 0 of an AB-1756 4-slot backplane.
Thank you for your feedback.
You changed your response to Not Helpful
You changed your response to Helpful
Collaborate with other users in our discussion forums
A valid service agreement may be required, and support options vary by country.